This Conventional Smoke Detector houses smoke sensor for monitoring the level of smoke in its surveillance. It switches to alarm state by communicating to the control panel when the level of smoke reaches its pre-set level. It communicates its zone number to the control panel for location tracking.
- Wide operating voltage
- Low standby current
- Drift compensation technique for false alarm immunity
- Insect-resistant screening
- Easy to maintain/service
- Dual bi-color LED indication for 360° viewing angle
Minimum 9V DC
Maximum 26V DC
12 mA at 12V
What is a smoke detector and how does it work?
Smoke detector is a measuring instrument that measures the level of smoke in its surveillance. It will raise an alarm only when the level of smoke exceeds its pre-set upper limit/threshold values.
Photoelectric/Optical Smoke detector work on a common light scattering principle. Smoke detector contains a chamber that consists of a light emitter usually a LED and a light a sensitive device like a photodiode that receives all the light directly emitted by the LED.
When the smoke enters the chamber, the intensity of light received by the photodiode reduces due to density of smoke. If the intensity of received light drops below a pre-set threshold level, fire alarm is triggered confirming fire.
Unit of measure for level of smoke is Obscuration/foot (Obs/ft).
Photoelectric smoke detectors are highly sensitive to visual particles of smoke and also respond quickly to smouldering fires.
Conventional smoke detectors are wired to the control panel using 2*1.5 sqmm copper cable. Their smoke sensitivity values are factory set and cannot be altered.
others in series
LHS Analog Cable
LHS Digital Cable